Room temperature sensor. (Thermistor)
Maintains the room temperature in accordance with the Setting Temp.
Indoor fan is delayed for 5 seconds at the starting.
Restarting is inhibited for approx. 3 minutes.
High, Med, Low, Chaos
--- Lights up in operation
--- Lights up in Sleep Mode
--- Lights up in Timer Mode
--- Lights up in Deice Mode or Hot Start Mode (only Heating Model)
--- Lights up during compressor running
(only Cooling Model)
Intermittent operation of fan at low speed.
The fan is switched to low(Cooling), med(Heating) speed.
The unit will be stopped after 1, 2, 3, 4, 5, 6, 7 hours.
The fan is switched to intermittent or irregular operation
The fan speed is automatically switched from high to low
The louver can be set at the desired position or swing
up and down, right and left (not on all models) automatically.
The setting temperature, indoor fan speed and desired
operation made are automatically set by fuzzy rule.
Operation ON/OFF by Remote controller
Sensing the Room Temperature
Room temperature control
Starting Current Control
Time Delay Safety Control
Indoor Fan Speed Control
Operation indication Lamps (LED)
Soft Dry Operation Mode
Both the indoor and outdoor fan
stops during deicing.
Hot start after deice ends.
The indoor fan stops until the
evaporator piping temperature
will be reached at 28°C.
Deice (defrost) control (Heating)
Hot-start Control (Heating)
Sleep Mode Auto Control
Natural Air Control by CHAOS Logic
Airflow Direction Control