View Panasonic NV-GS6EE / NV-GS6GC / NV-GS17E / NV-GS17EB / NV-GS17EG / NV-GS17EP / NV-GS18E / NV-GS21E / NV-GS21EB / NV-GS21EG / NV-GS21EK / NV-GS21EP / NV-GS25GC / NV-GS25GCD / NV-GS25GN / NV-GS28GK / NV-GS35E / NV-GS35EB / NV-GS35EG / NV-GS35EP / NV-GS35GC / NV-GS35G Service Manual online
allow service personnel´s to understand and service this model.
Please place orders using the parts list and not the drawing
followed by supplement service manual to be filed with original
VSK0581. Also, DE-974HA is supplied for VSK0644.
C.B.A., replace the assembly parts.
recorded tapes or discs or other published or broadcast
material may infringe copyright laws.
equipment to rain or moisture.
interference, use the recommended accessories only.
serviceable parts inside. Refer servicing to qualified service
for your safety and convenience.
replacement fuse has a rating of 5 amperes and it is approved
by ASTA or BSI to BS1362.
that it is refitted when the fuse is replaced.
replacement cover is obtained.
your home then the fuse should be removed and the plug cut
off and disposed of safety.
is inserted into any 13-ampere socket.
the following code:
may not correspond with the coloured markings identifying the
terminals in your plug, proceed as follows:
terminal in the plug which is marked with the letter N or
terminal in the plug which is marked with the letter L or coloured
connected to the earth terminal of the three pin plug, marked
with the letter E or the Earth Symbol.
which are important for safety. These parts are marked by
other hazards. Do not modify the original design without
permission of manufacturer.
the AC power line. Use a transformer of adequate power
rating as this protects the technician from accidents
resulting in personal injury from electrical shocks. It will also
protect AC Adaptor from being damaged by accidental
shorting that may occur during servicing.
overheated or damaged by the short circuit.
part on the equipment such as screwheads, connectors,
control shafts, etc. When the exposed metallic part has a
return path to the chassis, the reading should be between 1
and a good earth ground, as shown in Figure 1.
may be used to make the hot checks, leakage current must
not exceed 1/2 mA. In case a measurement is outside of
the limits specified, there is a possibility of a shock hazard,
and the equipment should be repaired and rechecked
before it is returned to the customer.