View Panasonic U-50PE2E5A / U-100PE1E8A / U-100PEY1E8 / U-125PE1E8A / U-125PEY1E8 / U-140PE1E8A / U-140PEY1E8 / S-100PU2E5B / S-125PU2E5B / S-140PU2E5B / S-71PU2E5B / S-100PF1E5B / S-125PF1E5B / S-140PF1E5B / S-71PF1E5B Service Manual online
of course becomes the object. But when mechanical
ventilation is installed interlocked with a gas leakage
detector in the smallest room where the density limit is
exceeded, the volume of the next smallest room becomes
ceiling is 2.7 m high)
floor space of the room according to the legislation on
refrigerant drainage. If there is no applicable legislation,
follow the standards described below.
requires a design that in the event of refrigerant gas
leaking out, its density will not exceed a set limit.
The refrigerant (R410A), which is used in the air conditioner,
is safe, without the toxicity or combustibility of ammonia, and
is not restricted by laws imposed to protect the ozone layer.
However, since it contains more than air, it poses the risk of
suffocation if its density should rise excessively. Suffocation
from leakage of refrigerant is almost non-existent. With the
recent increase in the number of high density buildings,
however, the installation of multi air conditioner systems is
on the increase because of the need for effective use of floor
space, individual control, energy conservation by curtailing heat
and carrying power, etc.
Most importantly, the multi air conditioner system is able
to replenish a large amount of refrigerant compared to
conventional individual air conditioners. If a single unit of the
multi air conditioner system is to be installed in a small room,
select a suitable model and installation procedure so that if the
refrigerant accidentally leaks out, its density does not reach the
limit (and in the event of an emergency, measures can be made
before injury can occur).
In a room where the density may exceed the limit, create an
opening with adjacent rooms, or install mechanical ventilation
combined with a gas leak detection device. The density is as
conditioners is 0.44
(1) No partition (shaded portion)
a door, or an opening 0.15% or larger than the respective
floor spaces at the top or bottom of the door).
Since refrigerant composition changes and performance decreases when gas leaks, collect the remaining refrigerant and recharge
the required total amount of new refrigerant after fixing the leak.
Some tools for R22- and R407C-type refrigerant systems cannot be used.
Liquid refrigerant should be
recharged with the cylinder
standing on end as shown.
and compressor defects. Due to the features of the refrigerant and refrigerating machine oil, the prevention of water and other
impurities becomes more important than ever.
moisture, or other foreign substances from entering. These substances can result in system
and pressure gauge are different.
To resist higher pressure, material must be
Use a conventional vacuum pump if it is equipped
with a check valve. If it has no check valve,
purchase and attach a vacuum pump adapter.
Leak detectors for CFC and HCFC that react to
chlorine do not function because R410A contains
no chlorine. Leak detectors for HFC134a can be
used for R410A.
For systems that use R22, apply mineral oil
(Suniso oil) to the flare nuts on the tubing to
prevent refrigerant leakage. For machines that
use R407C or R410A, apply synthetic oil (ether
oil) to the flare nuts.
Click on the first or last page to see other U-50PE2E5A / U-100PE1E8A / U-100PEY1E8 / U-125PE1E8A / U-125PEY1E8 / U-140PE1E8A / U-140PEY1E8 / S-100PU2E5B / S-125PU2E5B / S-140PU2E5B / S-71PU2E5B / S-100PF1E5B / S-125PF1E5B / S-140PF1E5B / S-71PF1E5B service manuals if exist.